Oct 14, 2019 - 09:39 AM
Most regulators do have some adjustment range for the outlet pressure. The MEGR-295 can be adjusted from the preset 11"WC up to about 13"WC, but the actual pressure that can be achieved consistently will depend on variables such as inlet pressure, flow rate, system piping configuration, etc. We do not have any other 2-stage regulators that would have a higher outlet pressure range. If I could find out these details about the application, I could make a better evaluation. Is this on an RV, where there is an appliance that is calling for higher pressure, or is it a different type of application?